Views:52 Author:hong Publish Time: 2020-11-19 Origin:TFW VALVE
The opening and closing part of the gate valve is the gate, and the movement direction of the gate is perpendicular to the direction of the fluid. The gate valve can only be fully opened and fully closed, and cannot be adjusted or throttled. The gate has two sealing surfaces. The two sealing surfaces of the most commonly used model gate valve form a wedge. The wedge angle varies with valve parameters, usually 50, and 2°52' when the medium temperature is not high. The gate of the wedge gate valve can be made into a whole, called a rigid gate; it can also be made into a gate that can produce a small amount of deformation to improve its manufacturability and make up for the deviation of the sealing surface angle during the processing. The plate is called an elastic gate. When the gate valve is closed, the sealing surface can only rely on the medium pressure to seal, that is, rely on the medium pressure to press the sealing surface of the gate to the valve seat on the other side to ensure the sealing of the sealing surface, which is self-sealing.
Most gate valves use forced sealing, that is, when the valve is closed, the gate must be forced to the valve seat by external force to ensure the sealing performance of the sealing surface. The gate of the gate valve moves linearly along with the valve stem, which is called a rising stem gate valve, also called a rising stem gate valve. Usually there is a trapezoidal thread on the lifting rod, through the nut on the top of the valve and the guide groove on the valve body, the rotary motion is changed into linear motion, that is, the operating torque is turned into operating thrust. When the valve is opened, when the lifting height of the gate is equal to 1:1 times the valve diameter, the fluid passage is completely unblocked, but this position cannot be monitored during operation. In actual use, the apex of the valve stem is used as a mark, that is, the position where it cannot be opened, as its fully open position. In order to take into account the locking phenomenon of temperature changes, it is usually opened to the top position, and then rewind 1/2-1 circle, as the position of the fully open valve. Therefore, the fully open position of the valve is determined by the position of the gate, that is, the stroke. In some gate valves, the stem nut is set on the gate, and the rotation of the handwheel drives the rotation of the valve stem to lift the gate. This kind of valve is called a rotating stem gate valve or a dark stem gate valve.
Company Name: Tianjin Tangfa Watts Valve Co., Ltd.
Contact Person: Mr. jack wang (General Manager)
+86 22 66224148
+86 22 25291233
RM 501-2, NO.1 Building,Tianhe technical Area
Binhai New area,Tinajin City,China